China Manufacturers Price Of 660v/220v Draw-Out Type Switch Cabinet Low Voltage Switchgear
GGD AC low voltage power distributing cabinet is applicable to power distribution system of AC 50HZ, and with a rated operational voltage of 380V,rated operation current to 3150A in power users like generators,transformer substation,and mining enterprises,and it is used in power transformation,distribution and control of driving motor,illumination and power distribution equipments.
Conditions for use
Ambient air temperature shall be neither above+40°C nor below-50°C.
Indoor installation and use,the altitude of the use venue shall not exceed 2000M
Environment relative humidity shall not exceed 50% at the maximum temperature of 40°C,high relative humidity is allowed when the temperature is comparatively low.(for example,it can be90% at +20°C).Also,the impact brought about by occasional condensation due to temperature change shall be taken into consideration.
The gradient to vertical plane shall not be more than 5 degrees when equipments installation.
Equipments shall be installed at places free from excessive vibration and impaction,and where no erosion shall be caused to the electric appliance components.
IF users have any special requirement,please negotiate with the manufacturer for settlement..
1. The shell is locally welded and assembled with 8MF cold-formed steel.Mounting holes arranged by E=20mm and E=100mm modules are arranged on the frame to improve the universality of product assembly.The panels and baffles are made of imported cold rolled sheet and adopt pickling, phosphating, electrostatic spraying, anticorrosive process.Cabinet internal treatment using hot dip galvanizing process.In order to strengthen ventilation and heat dissipation, the bottom and upper part of the cabinet have ventilation and heat dissipation holes, and steel wire mesh sealing cover, to prevent small animals to enter.For the convenience of lifting, the cabinet top four corners are equipped with rings.Considering the use of cable outlet, in the bottom of the cabinet set knock hole, and prepare to meet the construction drawing size requirements of the leather line sleeve.
2. When designing the GGD cabinet, the heat dissipation problem in the operation of the cabinet is fully considered.There are different Numbers of heat sink holes at both ends of the cabinet, when the electrical components in the cabinet heating, heat rise, through the upper end of the tank hole discharge, and the cold wind constantly by the bottom end of the tank hole supplement into the cabinet, make the sealed cabinet body from the bottom up to form a natural ventilation channel, to achieve the purpose of heat.
3, GGD ark according to the requirements of modern industrial product modelling design, the method that USES golden section ratio to design cabinet body appearance and the segmentation size of each part, beautiful and easy, face is new.Cabinet door USES turn axle activity hinge and frame to be linked together, installation, disassemble is convenient, the folding place of the door is embedded a hill model rubber model strip, the inlaid strip between door and frame when close the door has certain compression stroke, can prevent the door and cabinet body to collide directly, also raised the protection class of the door.The instrument door equipped with electrical components is connected to the frame with multiple strands of soft copper.Knurled screws are used to connect the installation parts and the frame in the cabinet. The whole cabinet constitutes a complete grounding protection circuit.
4. Electrical panels Basic Parameters
|Rated operating voltage
|Rated insulation volatge
|Horizontal busbar current rating
||1250 2000 2500 3200
|Vertical busbar current rating
|Max. feeder circuit current
|Max. drawer circuit current
|Max. control motor capacity
|Horizontal busbar peak withsatnd current
|Horizontal busbar short-time withstand current
|Vertical busbar peak withstand current
|Vertical busbar short-time withstand current
|Rated power freq. withstand voltage
|Secondary power freq. withstand voltage
|Enclosure protection degree
5. Order information
Schematic diagram of main circuit or electrical schematic diagram
Arrangement and layout
Model, specification and quantity of main components.
Incoming and outgoing wire method and cable specification, etc
If bus connection is required between the devices, bus connection and height from the ground shall be provided.
1. Indoor altitude above sea level: Maximum installation altitude: 2000m
2. Ambient air temperature: -5℃~+40℃ and the average temperature should not
exceed +35℃ in 24h
3. Relative humidity should not exceed 50% at max temperature +40℃. Higher
relative humidity is allowed at lower temperature. Ex. 90% at +20℃. But in view of
the temperature change, it is possible that moderate dews will produce casually.
4. No fire, explosion danger, serious pollution, chemical corrosion and severe vibration
5. Installation gradient not exceed 5°
6. This product is suitable for the following temperature transportation storage: -25℃ ~+55℃ 24h, in a short period of time (no more than 24hours) not more than+70℃.
This series of products with high breaking capacity, good dynamic stability, advanced and reasonable structure, electrical program of practical, series, strong versatility, various schemes of unit combination, a cabinet contained many circuits, save the area , beautiful appearance, high level protection, safe and reliable, convenient maintenance etc.
It accords with the standards IEC439 NEMA ICS2-322 as well as the GB7251-87 “Low voltage complete switch device ” national standards and ZBK36001-89 "low voltage withdraw type complete switch device” professional standards"