|Place of Origin:||China|
|Certification:||ISO IEC CB COC KEMA SNI SABS CCC|
Payment & Shipping Terms:
|Minimum Order Quantity:||1|
|Packaging Details:||wood pack|
|Delivery Time:||30 days|
|Payment Terms:||LC T/T|
|Supply Ability:||5000 piece/year|
|Body Material:||Coated Alluminum||Power:||AC|
|Frame Structure:||Metal Enclosed|
low tension switchgear,
low voltage metal clad switchgear
1.GGD type LV low voltage distribution cabinet is suitable for three-phase AC 50HZ, max voltage 380V, rated current to 3150Apower distribution system , it is widely used in power plants, substations, industrial and mining enterprises etc energy consumer and using for power, lighting and distribution equipment for electrical energy conversion, distribution and control purposes
2.Protection grade is IP30. IP20-IP40 could be optional acc to the requirements of service condition.
3.Good appearance. easy assembly and disassembly.
1. The shell is locally welded and assembled with 8MF cold-formed steel.Mounting holes arranged by E=20mm and E=100mm modules are arranged on the frame to improve the universality of product assembly.The panels and baffles are made of imported cold rolled sheet and adopt pickling, phosphating, electrostatic spraying, anticorrosive process.Cabinet internal treatment using hot dip galvanizing process.In order to strengthen ventilation and heat dissipation, the bottom and upper part of the cabinet have ventilation and heat dissipation holes, and steel wire mesh sealing cover, to prevent small animals to enter.For the convenience of lifting, the cabinet top four corners are equipped with rings.Considering the use of cable outlet, in the bottom of the cabinet set knock hole, and prepare to meet the construction drawing size requirements of the leather line sleeve.
2. When designing the GGD cabinet, the heat dissipation problem in the operation of the cabinet is fully considered.There are different Numbers of heat sink holes at both ends of the cabinet, when the electrical components in the cabinet heating, heat rise, through the upper end of the tank hole discharge, and the cold wind constantly by the bottom end of the tank hole supplement into the cabinet, make the sealed cabinet body from the bottom up to form a natural ventilation channel, to achieve the purpose of heat.
3, GGD ark according to the requirements of modern industrial product modelling design, the method that USES golden section ratio to design cabinet body appearance and the segmentation size of each part, beautiful and easy, face is new.Cabinet door USES turn axle activity hinge and frame to be linked together, installation, disassemble is convenient, the folding place of the door is embedded a hill model rubber model strip, the inlaid strip between door and frame when close the door has certain compression stroke, can prevent the door and cabinet body to collide directly, also raised the protection class of the door.The instrument door equipped with electrical components is connected to the frame with multiple strands of soft copper.Knurled screws are used to connect the installation parts and the frame in the cabinet. The whole cabinet constitutes a complete grounding protection circuit.
|Rated Working Voltage||V||400|
|Rated Current||Horizontal bus line||A||≤400|
|Vertical bus line||A||≤1000|
|Rated short-time tolerant current(1s)||kA||50|
|Rated peak tolerant current||kA||105|
|Rated Insulation Voltage||V||660|
|Out shell protection level||IP30/IP40|
conditions of use
1.The elevation shall not exceed 2000m;
2.The ambient air temperature is not higher than +40℃, and the average temperature within 24 hours is not higher than +35℃, the ambient air temperature is not lower than -5℃;
3.Atmospheric conditions the air is clean, the relative humidity does not exceed 50% when the temperature is +40℃, and the relatively high relative humidity is allowed when the temperature is relatively low.
For example, at +20℃, it is 90%;
4.No fire, explosion risk, serious pollution, chemical corrosion and violent vibration of the place;