|Place of Origin:||China|
|Certification:||ISO IEC CB COC KEMA SNI SABS CCC|
Payment & Shipping Terms:
|Minimum Order Quantity:||1|
|Packaging Details:||wooden case package|
|Delivery Time:||30 days|
|Payment Terms:||LC T/T|
|Supply Ability:||5000 piece/year|
|Name:||Electrical Switchgear||Feature:||Superior Performance, Product Safety, Reliability, Environmental Protection|
|Brand:||Power Distribution Transformer||Standard:||CE,ISO,UL,SABS,3C， IEC60076-11 ISO9001 ISO14001 KEMA CE|
|Model Number::||Electrical Switchgear|
KYN28-12 removable AC metal-clad switchgear (short for panel as below) is a new product. It will be a substitute for old fashioned metal-enclosed switchgear, such as KYN-12, JYN-12, GFC-12, etc. The panel applies to 3.6~12kV 3 phase AC 50Hz network for receiving and distributing power energy and also for control, monitor and protection. It accords with standard of IEC62271-200, IEC60694, GB3906.
|1||Rated impulse withstand voltage(Ump)||8KV|
|2||Main bus rated short withstand current (Icw)||30KA~50 KA|
|3||Distribution bus rated short withstand current (Icw)||30KA|
|4||Main bus rated current (InA)||1000 ~2500A|
|5||Distribution bus rated current (Inc)||1000A|
|8||Rated working voltage(Ue)||380V|
|9||Rated insulation voltage(Ui)||660V|
●Increase the heat capacity of the adapter, and significantly reduce additional temperature rise of connector, spacer plates due to the temperature rise in adapters.
●Clear and reliable division between functional units and compartments.
●Flat-mounted arrangement of bus bar permits good driving and thermal stability.
●The connecting with external cables is completed within the cable compartment, and the cable can be pulled in and out. The zero sequence current transformers are set in the cable compartment, easy for installation and maintenance.
●By the reduced current limiting reactors' matched short-circuit current, the bus bar's voltage could be stabilized at a certain value, the parts'short-circuit components strength requirement could also be reduced.
●The drawer unit has sufficient number of secondary plug-in components to meet the requirement for the numbers of connection points for computer interface and automatic control circuits.
Enter Your Message