|Place of Origin:||China|
|Certification:||ISO IEC CB COC KEMA SNI SABS CCC|
Payment & Shipping Terms:
|Minimum Order Quantity:||1|
|Packaging Details:||Standard wooden boxes for outer packing|
|Delivery Time:||30 days|
|Payment Terms:||LC T/T|
|Supply Ability:||5000 pieces/year|
|Product Name:||Box Type Fixed Metal Closed Switchgear / High Voltage Switchgear,Substation,outdoor Prefabricated Compact 11kv Substation,switchgear Outdoor Pre Installed Type Transformer Substation||Type:||Distribution Box Electrical Boxes,Box Type Prefabricated Substation|
|Rated Voltage:||10KV,40.5kV,13.2KV,10KV~40KV,6kv To 35kV||Frequency:||50/60Hz|
|Material:||Stainless Steel,Copper,aluminum-zinc Plate||Usage:||Power|
Outdoor Electric Compact Transformer Substation 33KV 400V YB Prefabricated Substation Used In Ethiopia Uzbekistan
YB-12/0.4 series prefabricated substation is suitable for AC50HZ, 6KVand 12KV power system, as a power of acceptance and distribution. It is widely used in industrial and mining enterprises, residential quarters, hospital, mall, high-rise buildings and other distribution systems.
The European type substation, is a complete set of new power transformer equipment developed by our company on the basis of transformation of national urban network making the optimal combination for the oil-immersed sealed power transformer and high and low voltage electrical components. Through structure optimization, the switchgear shall be miniaturized to extreme extent which greatly reduce the occupied area of the combined transformer with such advantages as small volume, low noise, reliable power supply, reasonable structure, blexible for installation, easy for operation and capable of going deep into the load center to maximum extent, etc.It can assemble network automation terminal (FTU) in the high-voltage ring network cabinet, realize the reliable detection of short circuit and single-phase grounding fault, and has the function of "four remote", which facilitates the automatic upgrade of network distribution. It is widely used in residential quarters commercial centers stations industrial and mining enterprises airports railroads schools hospitals, high-rise buildings and places.
· Use condition
1. The maximum ambient air temperature shall not exceed 45℃, and the minimum shall not exceed - 45℃;
2. The altitude shall not exceed 1000m. If special customized transformers and low-voltage components are used, the altitude can reach 4000m;
3. It shall be placed in a place with a vertical inclination of no more than 5°and no severe vibration or impact;
4. The air humidity is not more than 90% (+ 25℃);
5. Gas place without conducting dust, explosion hazard, corrosion metal and electrical components;
6. Outdoor wind speed shall not exceed 35m/s.
7. If the above normal use environment conditions are exceeded, the customer can customize it with our company.
· Structure characteristic
1. The box shell is designed according to the actual situation with reference to foreign advanced technology, and it has the characteristics of firmness, heat insulation and ventilation, stable performance, corrosion prevention, dust prevention, waterproof, small animal prevention, beautiful appearance, etc. There are many choices of shell materials, such as steel plate, composite plate, stainless steel plate, cement plate, etc.
2. There are high-voltage switchgear such as xgn15, hxgn17 or kyn28a and other equipment in the high-voltage room for high-voltage incoming line, high-voltage metering and high-voltage outgoing line. The high-voltage side can be arranged with ring network power supply, terminal power supply, dual power supply and other power supply modes, and high-voltage metering elements can also be installed to meet the requirements of high-voltage metering. The main switch is generally load switch or vacuum circuit breaker, with compact and reasonable structure and perfect anti misoperation function.
3. There are low-voltage switchgear such as GGD, GCS or MNS and other equipment in the low-voltage room for low-voltage incoming line, reactive compensation and low-voltage outgoing line. The low-voltage side adopts the panel type or cabinet mounted structure to form the power supply scheme required by the user, which can meet the power distribution, lighting distribution, reactive compensation, electric energy metering and other functions. The main switch generally adopts the universal circuit breaker or the intelligent circuit breaker, which is flexible in installation and simple in operation.
4. The transformer in the transformer room can use the fully sealed oil immersed transformer or dry-type transformer. The oil immersed transformer can be S9, S11, S13 or SH15, and the dry-type transformer can be scb10, scb11, SGB10 or scbh15. According to the actual needs of customers, it can be configured freely, which has the advantages of more selectivity and flexibility.
5. The cover of the box is designed with double-layer structure, and the interlayer is filled with foam plastics, which has good heat insulation function. The transformer room is equipped with anti condensation and automatic temperature control monitoring, heating and cooling devices. A dust-proof device is arranged on the position of the door sheet and the louver outside the side plate.
Note: Due to continuous product improvement, the dimensions provided in this sample are for reference only. If necessary, our company can design and produce according to user requirements. Please contact the company in time.
|Number||Item||Unit||FN12-12Load switch||FZN21-12Vacuum load switch|
|2||Maximum working voltage||KV||12|
|5||Rated breaking current||A||630|
|6||Rated thermal current (Virtual value)||KA/S||20/2||20/4|
|7||Rated dynamic current||KA||50||50|
|8||Short-circuit current (Peak value)||KA||50||50|
|9||Full-load breaking times||times||20||10000|
|11||1-min power frequency withstand voltage(phase to earthing)||KV||42||42|
|12||Lightning impulse withstand voltage(phase to earthing)||KV||75||75|
· Ordering instruction
1. Conceptual drawing or electrical schematic diagram of main circuit.
2. Model, specification and quantity of main components.
3. Incoming and outgoing line mode and cable specification, etc.
4. Shell material and appearance: composite plate, steel plate, stainless steel plate, cement plate, etc.
5. Other order requirements.