|Place of Origin:||China|
|Certification:||ISO IEC CB COC KEMA SNI SABS CCC|
Payment & Shipping Terms:
|Minimum Order Quantity:||1|
|Packaging Details:||wooden case|
|Delivery Time:||30 days|
|Supply Ability:||5000 piece/year|
|Standard:||High Voltage||Feature:||Practical And Durable|
|Product Name:||Metal-clad Switchgear||Rated Voltage:||12KV /24KV|
KYN28 middle-mounted high-voltage switchgear removable metal middle-mounted cabinet outlet cabinet customization
KYN28-12 (GZS1) indoor metal-fitted mid-shift open type switchgear (hereinafter referred to as the switch cabinet) is a three-phase ac 50Hz indoor power distribution unit, which is used to receive and distribute 3-12kv network power and to control, protect and monitor the circuit.The product CAN be installed on the panel of the relay chamber of various types of microcomputer type integrated relay protection devices, and CAN achieve intelligent control of the system, with remote control, telemetry, remote communication and remote control functions, CAN bus with communication interface to control the field network.It also has the function of preventing the wrong operation of the circuit breaker, preventing the trolley from pushing and pulling with load, preventing the electrifying closing grounding switch, preventing the grounding switch from sending electricity at the grounding position and preventing the electrifying interval from entering by mistake, which is referred to as "five defense".
|Rated Current of Circuit Breaker||A||630,1250,1600,2000,2500,3150|
|Rated Voltage of Switchgear||A||630,1250,1600,2000,2500,3150|
|Rated short-time withstand current (4s)||kA||16,20,25,31.5,40,50|
|Rated Peak Withstand Current (Peak Value)||kA||40,50,63,80,100,125|
|Rated Short-circuit Breaking Current||kA||16,20,25,31.5,40,50|
|Rated Short- circuit Closing Current||kA||40,50,63,80,100,125|
|1min Power Frequency Withstands Voltage||kV||24, 32, 42|
|Lightning Withstands Voltage , Rated Insulation Leve||kV||40, 60, 75|
|Protection Grade||Shell is IP4X, Shell is IP2X when compartment and circuit breaker doors are open|
1. The cabinet shell and baffle board of switch cabinet are made of aluminum-zinc steel sheet after CNC machining and bending, so the assembled switch cabinet can maintain the unity in size.Aluminum-zinc coated steel plate has strong anti-corrosion and anti-oxidation effect, and has higher mechanical strength than the same steel plate.The switch is divided into handcart room, bus room, cable room and relay meter room by partition board.The door of switch cabinet USES electrostatic spray to make its surface has the advantages of anti-collision, anti-corrosion, beautiful appearance (color can be determined by the user).
2. Handcart frame is made of aluminum-zinc coated steel plate after being riveted and welded by CNC machine tools: according to the purpose, handcart can be divided into circuit breaker handcart, voltage transformer handcart, isolation handcart, metering handcart, etc. Handcart of the same specification can be easily exchanged.Handcart in the cabinet from the limited position, test position and working position, each position is equipped with positioning device, in order to ensure that the handcart in the above position can not be moved arbitrarily, and the handcart must be moved to remove the interlock
3. The bus bar leads from one switch cabinet to another switch cabinet and is fixed by the branch bus bar and the static contact box.The flat branch busbar is connected to the static contact box and the master busbar by screw check without any other wire clip or insulator connection.The connection bolts on the busbar row can be insulated and sealed with end caps when required by the user and the project.When the bus goes through the switch cabinet partition, use the bus bushing to fix it.If the internal fault arc, can limit the accident to the adjacent cabinet, and can guarantee the mechanical strength of the bus.
4. The current transformer, ground switch, lightning arrester and cable can be installed in the cable room, and the seamed detachable aluminum plate can be prepared at the bottom of the cable to ensure the convenience of on-site construction.
5. The relay instrument room is used to install various components such as relays, meters, signal instructions, operation switches, etc. In addition, a small bus room can be added at the top of the instrument room according to the user's requirements, and 16 small bus bars can be laid.
Pressure relief device
6. In the handcart rooms, bus room, above the cable chamber is equipped with pressure relief device, when a circuit breaker or mistress line, cable, indoor internal arc fault occurs, along with the emergence of the arc, switch cabinet internal pressure rise, after reaching certain pressure, pressure release of metal plate at the top of the device will be automatically open, release pressure and discharge gas, to ensure the safety of operators and switchgear.
Conditions of use
1.Ambient air temperature: upper limit +40℃ lower limit general area -10℃;
2.Height: 1000 m;
3.Humidity: relative humidity: daily average is no more than 95%, monthly average is no more than 90%;
Water vapor pressure: daily average is not greater than 2.2KPa, monthly average is not greater than 1.8KPa;
Condensation may occur when the temperature plummets, accompanied by contamination. This product is suitable for the following two more severe than normal environmental conditions
(1).Infrequent condensation (no more than twice a month on average) with mild contamination;
(2) generally there is no condensation (no more than twice a year on average) with more serious contamination;
4.No fire, explosion hazard, or gases of sufficient severity to corrode metal and break insulation:
5.There is no place for violent vibration, jolting and vertical inclination not exceeding 80 degrees.
(1) allow storage and transportation at -30℃.
(2) if the altitude is more than 1000m, it should be handled in accordance with JB/2102 "technical requirements for high-voltage appliances in the altitude area". When the altitude is less than 2000m, the low-voltage auxiliary equipment does not need to take any measures
6. If the above normal conditions of use are exceeded, the user may negotiate with the company.