|Place of Origin:||China|
|Certification:||ISO IEC CB COC KEMA SNI SABS CCC|
Payment & Shipping Terms:
|Minimum Order Quantity:||1|
|Packaging Details:||wooden case|
|Delivery Time:||30 days|
|Payment Terms:||LC T/T|
|Supply Ability:||5000 piece/year|
|Model No:||XGN2||Rated Current:||630,1250,1600,2000，2500，3150|
|Rated Peak Withstand Current:||50,63,80,100,125KV||Rated Voltage:||3.6,7.2,12|
Xgn2 Type Modular High Voltage Switchgear, High Voltage Switchgear, High
and Low Voltage Switchgears:
♦ XGN2 box-type fixed metal- enclosed switchgear (hereinafterreferred to as equipment) is suitable
for 3.6 12 kV three-phase AC50Hz single bus or single bus band bypass power system, mainlyused
in power plants, substations, industrial and mining enterprisesand other distribution sites, as receiving
and distributing energy, andthe circuit is controlled, protected and monitored. This productconforms to
lEC60298, lEC62271-200, lEC62271-1,GB3906,GB/T11022, DL/T404 and other related standards.
♦ A variety of fixedvacuum circuit breakers can be used in the equipment, and GN30-12(D) rotary
disconnector or GN22-12 high current disconnector seriesproducts are used in the disconnector.
Due to the selection of newelectrical components, high technical performance, novel design,closure
between cabinets, separation and closure of instrumentroom, bus room, circuit breaker room and cable
room in cabinet, eachroom has independent natural ventilation (except instrument room),which has the
characteristics of reasonable structure, high safety andreliability, simple operation, convenient
maintenance and so on.
1. Ambient temperature: not higher than + 40"C, not lower than- 15uit breaking, and
within 24 hours its average.Temperature is not higher than +35 degree c, the equipment
should be used to reduce capacitywhen exceeding the above ambient temperature.
2. Relative humidity: the daily average is not more than 95%, andtic operation the monthly
average is not more than 90%.Number 3. Altitude: Usually the installation site is not more
than 1000m6, 7.2, 12KV) above sea level.The bureau should reduce its capacity in placeswith
an elevation of 1000m.nber
3. Earthquake Intensity: No more than 8 degrees.
4. The equipment should be installed without fire, explosion and violentvibration.No chemical
corrosion and other serious dirty places.6. If the above conditions of use are not satisfied, they
should besettled through negotiation between the user and the manufacturer.